If your electrical system contains circuit breakers that are controlled by GE MicroVersa Trip Solid State Trip devices, electrical operational testing can easily be performed using the General Electric TVTS1 Secondary Injection Test Set which has features to effectively test these breakers.READ MORE >>
With the critical role of circuit breakers, it is very important to periodically verify that they are performing as designed and intended. Numerous electrical circuits can potentially be compromised if a circuit breaker fails to trip when fault conditions occur. As with any new product, we expect it to work properly right straight out of the box. The unfortunate truth is that this isn't always the case. The same is true about circuit breakers.READ MORE >>
A secondary injection test is a method of verifying the electrical operational characteristics of a circuit breaker. While not specifically addressing components in the primary current path of a circuit breaker, secondary injection testing is used to verify operational settings and characteristics in the decision making portion of the circuit breaker (solid state trip device). This type of electrical operational testing can be conducted without the need for large, high powered primary injection test equipment. Since this method of testing only uses low level signals that the trip device would normally see from current sensor secondaries, it can also be less time consuming and generally safer than performing primary injection testing.READ MORE >>
If you maintain a power facility that has several kinds of protective relays, wouldn't it be nice to have a tool that can test most types of relays found in your system? This lets you save storage space and money on additional test equipment. If you are looking for a dependable relay tester, you might want to check out the ISA T-1000.READ MORE >>
Many circuit breakers are tested by use of secondary injection test equipment applied to the breaker’s trip unit. These specialty test sets check the trip function of the circuit breaker — in other words, whether the electronics in the breaker are functioning properly. When you have work requirements that involve testing and maintaining Merlin Gerin circuit breakers, the Merlin Gerin Secondary Injection Test Set is ideal for verifying the proper operation of the trip circuitry. Merlin Gerin is only one of several well-known brands in the Protec stable of test equipment rental.READ MORE >>
Regular testing and maintenance of circuit breakers and relays is essential when dealing with sophisticated electrical systems.READ MORE >>
For checking circuit breaker and protective relay systems, the secondary injection test set is an essential piece of electrical test equipment for companies to use. It differs from the standard primary injection testing method in that it does not require high current to be passed through the primary current path, but rather tests the breaker as a result of low level signals sent directly to the solid state trip device that controls the operation of the breaker.READ MORE >>
Circuit breakers should be tested on regular intervals to mitigate the risk of failure. A faulty breaker can cause a lot of problems if a fault condition were to occur. It is a good idea to have reliable tools that can thoroughly test the circuit breakers to avoid problems in the electrical system. One of the tools that offers complete diagnostic features for secondary injection testing of circuit breakers is the ABB PR010/T Secondary Injection Test Set.READ MORE >>
Low voltage molded case circuit breakers like the microprocessor-based SACE are often installed as protection devices for motors in industrial and commercial facilities. It is important to regularly check the condition of these devices because of the critical role that they have in protecting the electrical circuits that they are tasked with monitoring.READ MORE >>
The protective devices that are used for the oversight and operational decision making in low voltage circuit breakers (LVCBs) are are often simply referred to as a Solid-State Trip device (SST). They are essentially protective relays that are frequently an integrated part of a low voltage circuit breaker and monitor the primary current path of the circuit breaker. In normal operation, these solid-state trip devices will sense changes in the primary current path and make the decision to open the circuit based on the magnitude and duration of the fluctuation.
READ MORE >>
Secondary injection testing is a diagnostic method of determining if a secondary protective device will respond as expected in both normal and faulted conditions. This method of testing is conducted by injecting signals directly into the trip unit that controls that operation of the circuit breaker to which it is connected.
Since this type of operational testing is performed by injecting secondary signals into the device instead of using primary current levels, it is generally considered to be a safer method of verifying the proper operation of a circuit breaker. This method of testing can be performed on circuit breakers as a part of commissioning or preventive maintenance.READ MORE >>